Expert Local Home Services In Carmichael CA
CABS Heating & Air Conditioning is happy to provide expert local service in Carmichael, CA. Started in 2011, our company is family-owned and operated as well as dedicated to bringing you the best in home comfort services. Our HVAC services include AC and furnace repair, replacements, and maintenance. We also do plumbing & electric work!
We invite you to check out some of our reviews from others in Carmichael, CA. They’ll demonstrate our commitment to quality service with every job we do. Don’t wait – call CABS today at 916-375-1800 to get started now!
for Carmichael, CA
Our Reviews by City
Ed - Carmichael, CA 95608
Very professional, informative and friendly
First Class in every way!
Phil - Carmichael, CA 95608
Excellent evaluation service
Dale - Carmichael, CA 95608
After Ronnie’s inspection of my home’s current system plus our conversation in which I expressed my concerns, he seemed to know my home’s heating and ductwork needs. Not rushed and thorough.
Age: 23 yr RHEEM Size: 2.5 ton Location: gas pack roof Filter: 14x30x1 Work performed: heat tune up, system is operating at this time but slightly out of manufactured specifications due to inducer motor is running beyond max amps .64 of .62 amps and blower motor is also running above max amps 2.62 of 2.40 amps. Noticed some browning occuring on circuit board, cleaned flame sensor, spark igniter is good, blower is clean, pressure switch hose is clear from debris, tighten all wiring, performed a safety inspection on the heat exchanger to find hot spots and rust on some seams, evaporator coil is clean but very rusty and getting a temperature rise of 42 degrees. Work suggested A lot of parts are starting to fail. Looking from summer visit and this heating visit, start thinking about unit replacement.
5 year old amana split, side yard and attic. Talked with client about how it has been running.had a questions about thermostat reading 66 and heat set to 67 and the system wasn’t kicking on. Informed client that the system, is usually at a 3 degree difference before trying to engage heating or cooling. Client understood, 1 degree difference wouldn’t cause the system to fully engage. Called for heating and went into attic, filter is in great shape. Did end up noticing that the insulation in the attic is below insulation levels. Has rolled out r-11 insulation. R39 levels is what houses are starting with. Recommend adding or removing old insulation and blow in new insulation. Proceeded with tune up after attic inspection. AGE/MANUF:5 SIZE:4 LOCATION:attic FILTER:aa410 DUCTING:ok, some silver flex, some older ducting INSULATION R-VALUE:r-11 roll out WORK PERFORMED: Upon arrival the client stated that the system has been good. The filter is in a great condition. Ducting is sealed and i
Arrived on site for 1 year old Daikin split system installed by us, closet, and outside unit. Checked filter, filter is still in good condition. Checked blower and coil inside as well, both extremely clean and running well. All electrical tight inside the air handler. Cleaned off unit outside. AGE/MANUF:1, Daikin SIZE:4 ton LOCATION:closet, side yard FILTER:310 good DUCTING:ok INSULATION R-VALUE:good WORK PERFORMED: Upon arrival the client stated that the system has been running well . The filter is in a good condition. Ducting is sealed and intact.I removed the service panel from the unit. Tightened all electrical connections. CALCULATIONS: Blower motor was measured at .59 amps and was rated for 5.2 max amps. Blower wheel is clean. Indoor coil was clean. Return temperature was 69 degrees. Supply temperature was 85-90 degrees. Return static pressure was .2 WC. Supply static pressure was .03 WC. Outdoor unit is located by pool equipment . Removed the service panel from the unit. C
Additional work required before we schedule another appointment… Replace disconnect, strap down condenser and uv blanket
Furnace, ducting and insulation