Expert Local Home Services In Rancho Cordova CA
CABS Heating & Air Conditioning is happy to provide expert local service in Rancho Cordova, CA. Started in 2011, our company is family-owned and operated as well as dedicated to bringing you the best in home comfort services. Our HVAC services include AC and furnace repair, replacements, and maintenance. We also do plumbing & electric work!
We invite you to check out some of our reviews from others in Rancho Cordova, CA. They’ll demonstrate our commitment to quality service with every job we do. Don’t wait – call CABS today at 916-375-1800 to get started now!
for Rancho Cordova, CA
Our Reviews by City
Install Daikin fit 2.5 ton heat pump split closet ground Run new electrical Correct condensation drain with new Run main trunk line for back rooms New plenum
Installing 18.5 seer Bosch heat pump Curb Surge protector Iwave air purifier High flow 20x25x1 grille Zinsco breaker 50 gallon heat pump water heater Surge protector Run new electrical Zinsco breaker New 225amp solar ready electrical panel New breakers Seal insulate Drop existing ductwork Seal Insulation 1500 sqft
Arrived onsite for system tune up on heating side. Talked with tenant about the heating and how it has been going. System has been running well, per tenant did ask when filter was last changed, explained to me that filter was changed last year, and hasn't changed it. Pulled filter and removed, let client know this needs to be replaced every month. Due to the amount of people inside the house. Tested blower motor, tested out at 7.77. Noticed a lot of build up on motor. Also noticed ac coil starting to show rust. Would start to look into replacement options for this system. As it is starting to show ware and tare on system. Blower motor and copper showing issues.
All estimates are for work that I noticed when on site when dealing with the Diag. Noticed first that the system was throwing error code 3 flashes at the board, stating pressure switch unable to close. After further investigation could see burning on the control board as well. Burnin on control board potentially could be send wrong readings saying that the pressure switch isn’t closed. Or the inducer motor is not able to pull pressure switches closed due to older motor, blockage in motor, or blockage in flue of system. Thirdly, pressure switch could also be failed as well, causing he system to not read correctly to fully go through sequence of operations during heating. When client stated that it was heating the morning of, more points to intermittent failure with board, and motor. Left estimate for all 3 components that I noticed to be having issues
Arrived onsite for tune up, ended up being a diag, informed client what would happen if no heat. Didn’t engage heat due to issue with pressure switch and burning on control board, as well as inducer could not be pulling enough vacuum anymore and failing.left quotes for repairs for boards and pressure switches, let client know the system is in fact not heating properly but intermittently heating.
Arrived onsite for 7 year old gas pack unit on roof. Talked with client about system, had client turn on heat for me, also asked about filter replacement, client is on top of filter replacement. Visual inspection was good, did notice small burn marks on control board on pack unit, at the resistors, let client know about visual inspection. Did end up going thru with tune up after inspection for client, system is running well. Noticed during turn up static pressure was a little on the high side, client stated that some registers are closed, informed the, the causes of closed registers on the system and the issue it could cause. Client opened registers before I left. AGE/MANUF:7 Bryant SIZE:3 ton LOCATION:roof FILTER:ok DUCTING:ok INSULATION R-VALUE:ok WORK PERFORMED: Upon arrival the client stated that the system has been running well . The filter is in a good condition. Ducting is sealed and intact.I removed the service panel from the unit. Tightened all electrical connections