Expert Local Home Services In Rio Linda CA
CABS Heating & Air Conditioning is happy to provide expert local service in Rio Linda, CA. Started in 2011, our company is family-owned and operated as well as dedicated to bringing you the best in home comfort services. Our HVAC services include AC and furnace repair, replacements, and maintenance. We also do plumbing & electric work!
We invite you to check out some of our reviews from others in Rio Linda, CA. They’ll demonstrate our commitment to quality service with every job we do. Don’t wait – call CABS today at 916-375-1800 to get started now!
for Rio Linda, CA
Our Reviews by City
22 year old furnace that has control board issue along with blower motor leaking oil as well. Client mentioned issue with fresh air intake, but is taking care of it himself. Informed client about installing new board and pricing, with blower motor as well. Ended up looking at condenser outside, condenser has been replaced with a Coleman condenser, but 22 year old furnace hasn’t been replaced. Went over options about pricing with just furnace as condenser is newer. Having comfort advisor today to go over options for new furnace.
AGE/MANUF:3 year, Lennox SIZE:2.5 LOCATION:garage side yard FILTER:poor pleated DUCTING:silver flex INSULATION R-VALUE:r39 WORK PERFORMED: Upon arrival the client stated that the system has been running very well. The filter is in a poor condition. Ducting is sealed and intact.I removed the service panel from the unit. Tightened all electrical connections. WORK SUGGESTED: recommended installing surge protector on both the air handler and condenser, as well as blower cleaning. Recommend joining maintenance plan CALCULATIONS: Blower motor was measured at 1.23 amps Blower wheel is clean. Indoor coil was Clean. Outdoor unit is located back yard . Removed the service panel from the unit. Cleaned all debris from the electrical compartment. Tightened high voltage on the contactor switch. Contactor pads are Good. The unit is equipped with a 35/5 MFD capacitor. The 35/5 Capacitor is rated for a +/- 5 % and was measured at 33.64/4.26MFD. Outdoor fan motor is rated for 0.7 max amp